Elite Software combines all of the hvac design manuals into one simple to use Cad That’s a Plan”, “Hit the Load J”, “Basic Duct Principles”, and “CHVAC ”. chvac logo Commercial Load Calculation Software. Calculates heating and cooling loads for commercial applications, compliant with ASHRAE Standard Elite Software Chvac Medical Gas and Vacuum Systems Handbook NFPA Health Care Facilities The B-Line series Cable Tray Manual
|Published (Last):||15 February 2008|
|PDF File Size:||17.70 Mb|
|ePub File Size:||19.67 Mb|
|Price:||Free* [*Free Regsitration Required]|
Title “Fan and Duct Loads” is somewhat misleading, it should probably be written something like “Duct loads in winter” and “Fan and Duct Loads in summer”, but so many words would not fit in the report layout. Digital Transformation may be defined in a number of different ways by analysts or enterprise software vendors. And this is a picture of an Elite report for the same AHU http: Red Flag This Post Please let us know here why this post is inappropriate. If you have set the Softtware Unlinked property to True for any supply runout in the system, its Flow Discharge property is then user defined, and therefore may not be equal to the airflow calculated for the room.
Elite Software Chvac 8.02.32
Check your sensible and latent loads. Check your component dimensions for each room on the Room Data page and check that they have been entered using the right units. What is a system? You have to save “clever” work for yourself. Elit just want to know chavc is right. I have learnt a great deal. What did you put in “motor efficiency” or something like that in air handler settings screen in chvac?
Call Elite Software at oror visit www.
Getting Started > Frequently Asked Questions
The one load factor averages sotfware varying heat gain during the day for that orientation. Chvac does give you overview of all loads in good manner. Close this window and log in. Therefore, you need to place the people where you expect them to be when the peak load occurs.
You can calculate reheat in Elite psychro module and add it to chvac air system. I used at least half dozen of calculation software and don’t like much those who try to do work for you, in more complex projects such automatism can cause nasty errors.
How do I handle an inclined roof? Sofware likely does not reduce loads but only adds it. mankal
You can assign a zone and a system for every room in your project see Room Data topic. Latent loads from bathrooms and sensible equipment loads from televisions are two such examples. ACCA Manual J is a residential load calculation procedure that makes many simplifying assumptions so that it chvvac reasonably easy to perform manual heat gain and heat loss calculations. Such approach works only in areas where engineer’s responsibilities are not defined.
I always leave it, i. Are you an Engineering chvca
Another reason for excessively high loads could be windows. Why do the reports do not show net tons or recommended tons? Maybe Chgac am becoming too “old school”, but sometimes on these forums try to sharply point out to young engineers to not expect software packages to do design work for chgac. It’s easy to join and it’s free.
You can also obtain load reports for every system and zone in your project see the Select Reports topic. We recommend that you add Btuh for each bathroom and washroom.
By “hidden” sensible and latent loads, we mean loads that are present but might not necessarily be obvious to a new user.
We do not recommend that you grossly oversize a unit, but we do recommend that you adequately size the unit to handle some unexpected loads. In Rhvac Online, a zone is a group of one or more rooms.
Elite Software Chvac | موقع مهندسى الكهرباء والميكانيكا العرب
By conservatively, we mean be critical about rating a house as having “tight” construction. Why does changing the direction of a roof not affect the roof’s loads?
Thus, it is appropriate for all commercial applications. A load is a load. Rhvac Online is based on Manual J and is intended primarily for detached residential buildings. Some of the main items are building dimensions, infiltrations, people, and “hidden” sensible and latent loads. I will try to look at it when reaching HAP. I entered a ventilation value in the Room Data screen, but my results don’t show this ventilation.
Since the ratio of a room’s sensible gain to the sensible gain of the system is probably not equal to the ratio of the rooms sensible loss to the sensible loss of the system, the rooms’ heating and cooling airflows are probably different, so the sum of the room airflows may not equal that of the system.
They do not car about official standards much.